View and Download Baxi Bahama user operating instructions manual online . Gas Fired Wall Mounted Combination Boiler. Bahama Boiler pdf manual. Boiler Manuals for the Baxi Bahama SIT appliance. Gas Fired Wall Mounted Combination Boiler Installation and Servicing Instructions. BAXI. Page 2. Natural Gas Baxi Bahama G.C.Nº 47 Baxi Limited.
|Country:||Trinidad & Tobago|
|Published (Last):||26 August 2005|
|PDF File Size:||10.95 Mb|
|ePub File Size:||10.67 Mb|
|Price:||Free* [*Free Regsitration Required]|
Dirty or loose thermocouple connections – defective thermocouple – defective flame safety magnet – incorrect or faulty wiring – overheat cut-off device defective – adverse wind conditions – incorrectly filled terminal – partially blocked pilot injector. Clean the debris from the filter. Wall mounted powered flue condensing gas fired central heating boiler 52 pages.
Water section diaphragm faulty. This is available direct from Baxi Heating. Ensure that the filling loop is connected and open, then open the heating flow and return valves on the boiler.
Baxi Bahama 100 SIT
Read the instructions fully before installing or using the appliance. Follow the lighting instructions located on the bottom cover or refer to the “Instructions for Use”.
When correct the burner ignition should be smooth and quiet when a hot water outlet is opened. Dismantle clean and manula using Dow coming silicone grease. Gas pressure too low. Fitting The Outer Case Gas isolation valve partially closed. Incorrect or faulty pilot injector fitted – pilot injector partially blocked. Thermocouple worn out or damaged. Your Baxi Bahama is a gas fired, room sealed, powered flue combination boiler, providing central heating for your home and mains fed domestic hot water to taps and shower.
BAXI COMBI HE PLUS OPERATING INSTRUCTIONS MANUAL Pdf Download.
Insert the two fixing screws into the sides of the chassis Fig. Gas isolation valve closed. Check and clean gas filter, also check gas inlet pressure. Temperature selector set to ‘1’. Energy cut-off device may be faulty. The following guidelines indicate the general requirements for siting balanced flue terminals. Pilot flame will nor light or stay lit.
Slow ignition screw incorrectly set will also cause a high water rate. Turn selector to ‘5’. Commissioning The Boiler Checklist will be required in the event of any warranty work. Use the Baxi Multipoint BF Fault Finding table below to determine the problem with your boiler and if necessary identify the replacement parts you need. Loose screws at joints or fittings – detective “O” ring damaged valve casting at joint – defective burner feed pipe.
Use the fault finding troubleshooting manual to solve your Baxi Platinum Combi Boiler issue. To prevent seizure, the pump will operate for approximately 1 minute if it has not run in the last 24 hours. Open the cold feed to the boiler. Replace any faulty components found.
Comments to this Manuals Your Name. Baxi UK Limited provide a 12 month guarantee on the boiler. The minimum clear spaces needed around mm both sides will the boiler measured from the casing are as be necessary when the optional security screws You can diagnose the issue and find your replacement parts.
The guarantee operates from the date installation is completed for the customer who is the original user. Check the electrode lead is routed clear of all metal parts.
Got it, continue to print. Incorrect pilot lighting procedure. Exchange push rod and seals. If the system design requires an output other than this, proceed as described below.