LRM-AS/LRM (Wall Mounted Back to Topics · LRM-AS/LRM Product Overview · How to wire LRM-AS and LRM · How to replace/reset. Evolve LRM-AS Series , Rel. Instructions. LRM-AS by Evolve Guest Controls Inclusion of the LRM-AS Wall Mounted Dimmer on the EHC Wireless. Scene Command Class. – Security Compatible – Supports the Powerlevel command. – Has automatic Static Update Controller (SUC) capability. LRM-AS.
|Published (Last):||19 April 2011|
|PDF File Size:||19.59 Mb|
|ePub File Size:||11.42 Mb|
|Price:||Free* [*Free Regsitration Required]|
I figured it out.
I initially tried to attach the dimmer to one of the wires from the group of neutral wires. I often had to remove the yellow wire and trim the green wire in order to get them to fit.
In my house, I usually had to run a new wire from the switch’s electrical box to the fixture the switch controlled so that I would have a neutral available for the switch.
The white wire connects to the neutral coming back from the load and returning to the load center breaker box. I removed the paint from the other wires but they are all black so I need to determine which one is line and which one is load. The Evolve switches are not complicated to wire, but with all the extra wires they take up a great deal of space in a switch box. Ill pick up a wire tester to figure out what the wires are.
Now I just need to finish installing the other dimmers. Please login or register. You need to determine accurately the function of evolce wire in order to install the switch safely. The neutral wires were pig tailed together with a wire connector on the end. Evolve has several names.
Evolve LRM-AS – Wall Mounted Dimmer – White
Thanks for the response. The yellow wire is not needed, except if you want to have the equivalent of a 3-wire circuit. Since you are replacing an existing switch, you should not have to worry about running a neutral to the load because it is already in place.
I twisted the neutral wire from the dimmer in with the others and added a wire connector. Did you miss your activation email? In one photo, I see several wires twisted together. In that case the other black wire is load. If that is the case, then it should be rather easy to determine which of the two black evilve is line using a circuit teste.
If those twisted wires are neutrals, that’s where the white wire would connect, if they’re part of your light’s circuit. I would appreciate any help that you guys can provide. You need a neutral usually white in the U. My switch box only has 3 wires going to the current light switch. What the wiring diagram is telling you is that you need to provide a neutral wire to the switch and a efolve wire to the load. I can’t really tell what wire colors you have because of the paint.
Evolve seems to be the brand name for ACT’s residential line of products.
You are right about the twisted wires. I took a look at them after you mentioned it. Have a look here.
Help with Evolve LRM-AS as 3-way
I’ve attached images of the wires. The wiring diagrams for Evolve switches can be confusing. One is the lrmas and I assume the other two are the line and load but I am not sure.
I had to attach the neutral to the group of neutral wires.